|Size||4,760 x 1,200 x 2,250(LxWxH) mm|
|Stacking Frame||6,060 x 2,440 x 2,590(LxWxH)|
|Compressor||2 Bitzer Screw (2 circuits) 6 step capacity|
|Refrigerant||(Zero ozone deletion potential) HFCR134A|
|Fluid Flow||56/386.4m3/hr min/max|
|Max Power Absorbed||435kW|
|Electrical Supply Voltage Phase||400V|
|Max Current Absorbed||705 (625 Nominal)A|
|Chiller Power Connections||M12 Lugs|
|Sound Pressure Level||73dB(A)|
Related Case Studies
Read how we have made it work for related businesses.
The situation was getting ‘hot hot hot’ at a major shopping destination in the north of England when the main air conditioning system failed during a heatwave.View Case Study...
An international food and drink supplier of canned fish called in ICS Cool Energy as existing process air conditioning systems failed to cope in 35°CView Case Study...
Ambitious expansion plans to double capacity meant that a major Herefordshire cider producer needed expert help with essential tepmperature control.View Case Study...
It was ‘stop press’ for a major printing company when the site’s chiller failed in the middle of the night. Rapid response and solution was neededView Case Study...
Data Centres are integral to everyday life and ICS Cool Energy has a comprehensive range of high capacity, energy efficient solutionsView Case Study...
Turkey is the top choice in around 75% of all homes to help celebrate Christmas but delivering the best birds to our tables is a special challenge for the producersView Case Study...